Fjärrkylerörsystem - Fabrikstillverkade flexibla rörsystem - Del 3: Medierör av plast utan fast förband mellan värmeisolering och medierör - Krav och provningsmetoder
This document specifies requirements and test methods for factory made thermally insulated non bonded flexible pipe-in-pipe assemblies for directly buried district cooling distribution systems, comprising a service pipe from DN 15 to DN 200 and a casing of polyethylene. The pipe assembly may also include the following additional elements: measuring wires, spacers and diffusion barriers.
This document is intended to be used in conjunction with prEN 17414-1 ).
This document applies only to insulated pipe assemblies, for continuous operation with water at various temperatures (1 to 30) °C and a maximum operation pressure of 25 bar dependent on material specified.
The design is based on an expected service life with continuous operation of a minimum 50 years.
This document does not cover surveillance systems.
NOTE For the transport of other liquids, for example potable water, additional requirements may be applicable.