Provning av brandmotstånd - Icke bärande byggnadsdelar - Del 5: Överluftsdon
This European Standard specifies a method for determining the fire resistance of air transfer grilles (ATG).
It is applicable to air transfer grilles intended for installation in building components (typically walls, floors or ceilings). The orientation of the installation of the air transfer grille can be vertical or horizontal.
The closing mechanism of the air transfer grille can come from expansion of material and/or from any mechanical or electrical closing device.
This test method is valid for fire resistant or fire resistant and smoke control air transfer grilles.
An additional test configuration is valid for fire resistant or fire resistant and smoke control air transfer grilles in applications where flame impingement is a risk during open state from start of fire (Annex A).
This test method evaluates the behaviour of the air transfer grille when exposed to the standard fire curve described in EN 1363-1 and the standard pressure described in EN 1363-1. It is not the intention of this test to provide quantitative information on the rate of leakage of smoke and/or hot gases or on the transmission or generation of fumes under fire conditions. Such phenomena are only to be noted in describing the general behaviour of test specimens during the test.
The rate of leakage of smoke at ambient temperature or at 200 °C as an optional requirement for ATG with declared smoke control will be confirmed in accordance with standard EN 1634-3.
This test method is not valid for determining the fire resistance of air transfer grilles that are used in ducts because ATG are considered as separating elements. The test method for ATG, used in ducts is described in the corresponding duct standards.
This test method is not valid for determining the fire resistance of a fire damper or a fire barrier connected to a duct on either or both sides because an ATG is tested as a fire-separating element on its own. Fire dampers are tested according to EN 1366-2. Non-mechanical fire b ...